SAN MAO TECHNOLOGY CO., LTD.
HOW IT WORKS
PH type-Dust Application
Filter Area 3,000 s.f./278m²
(The air of space circulate six times per hour.)
Magnetic Switch with manual air pluse jet cleaning button
3-stage filtration system
Water Release Device
Optional HEPA filter
Stage 1. ＞
Capturing larger particle
Stage 2. ＞
Cartridge Filter x 2
Being coated with TEFLON, featuring 99% of 1 micron filter efficiency
Stage 3. ＞
Removing peculiar smell and smaller particle
Manua pluse Cleaning
Easy-access door for maintenance.
Cartridge:99%of 1 Micron filter efficiency
Heavy gauge power coated steel.
Adjustable inlet 1x 27 inch (26 x 686mm)
Unit could install Ø8”x2 fume arm or tube with fume hood.
＞ HEPA Module
＞ Efficiency 99.995%
Spec.: 24 x 30 x 8 inch (610 x 762 x 205 mm)
We reserve the right to make changes in SmartVent products in order to improve design or performance characteristics without further notice.
HOW IT WORKS
AC-3000PH Airflow Directions
Fume extracted via inlet 1 or 2, and passing through the Aluminum Mesh 3, for seizing larger particles.
The air is being conducted to Cartridge filter as 99% 4 of 1 micron particle filtration.
The remaining dust are the n filtered through the carbon filter. 5
As air slowing down inside the upper chamber, partical will fall down onto the drawer of dust collector.
Clean air is returned back to the workplace.
No.1, Lane 119, Section 3, Dafeng Rd., Tanzih Dist., Taichung City 427, Taiwan